The Automist Smartscan circuit should be clearly labelled (a sticker is provided for this purpose and is placed during commissioning). Automist Smartscan requires an independent 230V a.c. / 50Hz electrical supply, not shared with other unrelated devices. The Automist system, fire detection and alarm system may use this circuit, which must remain powered in the event of a fire. When prepay meters are present an additional prepay meter should be added specifically for Automist and charged with credit beyond its expected lifetime use as part of the maintenance cycle.
For more details see: