Compatible wired detector Important! - The total number of wired detectors in a system must be 6 or less! The number of wired detectors in a series chain must be 3 or less! Important! - caps must stay on detectors until occupant moves in! Important! Always follow the manufacturer’s instructions when installing wired detectors. A 24 volt wired connection shall be made between the detector and the spray head location using fire protected cable.
ONLY the following wired detector is compatible with the Automist system:
Apollo Orbis ORB-OH-13001-APO Multisensor detector. https://www.apollo-fire.co.uk/products/range/orbis/smoke-heat-detectors/orb-oh-13001-apo-orbismultisensor-detector
ONLY the following wired detector bases are compatible with the Automist system:
Apollo Orbis TimeSaver Base ORB-MB-00001-APO. https://www.apollo-fire.co.uk/products/range/orbis/mounting-bases/orb-mb-00001-apo-orbistimesaver-base-with-continuity-switch
Apollo Orbis TimeSaver LX Base ORB-MB-00002-APO. https://www.apollo-fire.co.uk/products/range/orbis/mounting-bases/orb-mb-00002-apo-orbistimesaver-base-lx-without-continuity-switch
"Important! For wired detector, you must fit an End of Line (EOL) resistor across the OUT+ and COM- terminals in the detector base. Resistors should be 4.7k ohm, 0.5W, 1%, such as Multicomp MF50 4K7. EOL resistor must only be added to the last detector in the chain. http://uk.farnell.com/multicomp/mf50-4k7/resistor-0-5w-1-4k7/dp/9340629