Can you install Automist Smartscan Hydra in a room with a hob or a woodburner or stove? Technical Support March 13, 2019 16:46 Updated Follow Yes, but the spray head must be positioned at least: 1.5m away from any hob 3m away from any log burners or small fireplaces Related articles How deep does a nib or pillar need to be for it to become a preferred installation position? What are the dimensions of the Hydra controller? Is Automist Smartscan Hydra WRAS Approved? What is the specification of the wireless Hydra alarm? How much clearance should be left around the Smartscan Hydra Head? Comments 0 comments Please sign in to leave a comment.