When Automist Smartscan Hydra is powered up for the first time the YELLOW LED will remain solid and the system will chirp to indicate that the system has not been commissioned. Commissioning is a simple programmed procedure that allows Automist Smartscan Hydras response to fire to be tested in situ. During commissioning, the alarms sound, the sensors are tested, the pump runs for 60 seconds and the output pressure and water flow are monitored. Commissioning is required:
Once all the components of the system have been installed and the system is powered.
As part of a yearly maintenance cycle.
If plumbing or construction work takes places, new alarms are installed, or maintenance work occurs which could affect the system.
Commissioning must be performed annually by an Authorised Automist Smartscan Hydra Installer.
For more details see: